Question What code was the requirement to use in use covers in? What code dis allowed the feeding of an outdoor receptacle from the kitchen small appliance circuits. Thanks Dave Retired Master Electrician
Answer Section 210.52 (B)(2) states: NO OTHER OUTLETS. The two or more small-appliance branch circuits specified in 210.52 (B)(1) shall have no other outlets.
Section 406.9 (A) relates to receptacles in damp locations.
Section 406.9 (B) relates to receptacles in wet location.
About Electrical Wiring in the Home
This site answers questions related to home electrical wiring, home wiring, general electrical help,and other electrical questions related to aleternating current (AC). You can find help on the National Electical Code, home electrical issues, wiring electrical outlets, installing lighting, electrical grounding, and general electrical help for do-it-yourself projects not require an electrician. If you do not see your home electrical wiring question answered in this area then please ask your electrical wiring question here
General electrical wiring, including but not limited to, residential, panelboards, control wiring, low voltage wiring, Heating and A/C control wiring, single and three phase wiring.
I have been doing electrical since high school. I have been licensed by the State of North Carolina for ten years and am currently the Building Maintenance Superintendent for a municipality. I have extensive control wiring experience.
Organizations Refrigeration Service Engineers Society.