Electrical Wiring in the Home/Higher Than Rated Voltages In Electric Mains
QUESTION: This relates to a typical problem unionised power-utilities labour can cause for hapless consumers in the third world. I have a 4 wire, 3 phase (240V 50Hz) power connection to my residence. Of late, there's a mismatch in voltages (phase to neutral) in the three different phases as measured right at the input terminals of the energy meter. The phase to phase voltages are uniform. When measured against a ground terminal, the neutral shows a voltage between 40 to 3 V. Individual phases can record voltages as high as 280-290V, causing voltage stabilisers, wherever connected, to trip off or for appliances/lighting fixtures to get damaged. I suspect the fault lies in the distribution of the state utility, but rather than getting into a slanging match with that lot, is it possible to correct the voltage in the neutral line by earthing it through some grounding arrangement?
ANSWER: Sounds like a bad neutral connection
This could be anywhere between your service panel and the transformer
[an error occurred while processing this directive]---------- FOLLOW-UP ----------
QUESTION: Thank you for the reply. It is most certainly from the electric pole to the transformer of the utility, perhaps from the transformer onwards. It could be some internal fault with the transformer. But the query really is, is there some means to earth the voltage that develops in the neutral wire, some sort of cut in device that would detect a higher than a threshold limit of voltage in the overhead neutral and divert it into the ground?
Sorry, but it doesn't work like that.
The only alternative to getting the utility to fix their problem would be to install a transformer at your end which transformed only the three phase legs and had a secondary winding neutral which would eliminate the need for the utility neutral. I don't know if they allow that there, but is not a project for any but the most highly skilled tradesman.
About Electrical Wiring in the Home
This site answers questions related to home electrical wiring, home wiring, general electrical help,and other electrical questions related to aleternating current (AC). You can find help on the National Electical Code, home electrical issues, wiring electrical outlets, installing lighting, electrical grounding, and general electrical help for do-it-yourself projects not require an electrician. If you do not see your home electrical wiring question answered in this area then please ask your electrical wiring question here