Electrical Wiring in the Home/GFI help
QUESTION: Trying to change out old GFI. New one is cold. I noticed both black wires are hot and one white wire is cold. The last wire that is white is cold. So. Having issue with load vs line.
I assume you don't know which wires are which. With the power off, disconnect the wires. Then turn the power back on, carefully without touching the wires, use a tester, see which pair of wires show power. You should not see power in both sets. Obviously, the set with power will be the line.
The GFCI will be marked, as far as which is the load and the line.
---------- FOLLOW-UP ----------
QUESTION: That's the strange part. I have two black wires hot and one white wire hot. The remaining white wire is cold. I don't see an extra terminal for 3 line wires, Only for two line and two load.
Have you disconnected all of the wires? If you do not disconnect all the wires, you will get feedback. If you have disconnected all of the wires, and still getting a hot reading on both black wires, then you have some major problems with your wiring, and an electrician would have to figure out what is wrong.
About Electrical Wiring in the Home
This site answers questions related to home electrical wiring, home wiring, general electrical help,and other electrical questions related to aleternating current (AC). You can find help on the National Electical Code, home electrical issues, wiring electrical outlets, installing lighting, electrical grounding, and general electrical help for do-it-yourself projects not require an electrician. If you do not see your home electrical wiring question answered in this area then please ask your electrical wiring question here